- BrandНПП «МАГНИТО-КОНТАКТ»
- Country of manufactureRussia
Certificate of Conformity to the requirements of Technical Regulations (Technical Regulations on Fire Safety Requirements, GOST R 53325 - 2012) No. SSBK RU. PB25.B.03306 . Valid from 22.09.2015 to 21.09.2020
The siren is designed to alert people about fire or alarm by means of a light signal. The degree of protection of the enclosure of the siren is IP66 in accordance with GOST 14254. Nominal supply voltage: - 12V DC. The product class according to the degree of protection of a person against electric shock is III in accordance with GOST 12.2.007.0.
The annunciator is a monoblock containing a light glass. Inside the case OS - 12 "AYAKS" isp.01 there is a printed circuit board with radio elements with two duplicated switching terminal blocks for connecting external power. The case of the OS - 12 "AYAKS" siren isp.01 is equipped with two hermetic glands, which provide connection of a cable with a diameter of 6 to 14 mm. The case of the OS - 12 "AYAKS" siren isp.02 is equipped with a KSPVG 2x0.2mm terminal, 1 meter long, there are no terminal blocks on the board.
Main technical characteristics
|Siren name||Annunciator OS - 12 "AJAX"|
|Supply voltage range, V||9 - 13.8|
|Maximum consumed current, no more, mA||thirty|
|Sheath protection degree||IP66|
|Operating temperature range, ° С||from - 55 to + 70|
|Relative humidity, %||98|
|Overall dimensions, no more than, mm (LxHxT)||157 x 121 x 50|
|Weight, no more, kg||0.6|
When working with sirens, safety measures must be taken in accordance with the requirements of the "Rules for the Operation of Consumer Electrical Installations" (EPEP).
When repairing, installing and operating the siren, it is necessary to take safety measures in accordance with the "Rules for the technical operation of consumer electrical installations" and "Safety rules for the operation of electrical installations of consumers".
Installation on site
The siren is installed on walls or other structures of the room in places that provide contrast perception of the light glass in natural and artificial lighting from a distance of at least 5 m, as well as exclude the ingress of dirt. Before installation, marking is made for fixing the case to the wall (Fig. 1).Fig. 1 Overall and installation dimensions of the OS - 12 "AYAKS" siren, version 01 Fig. 2 View without cover Fig. 3 Overall and installation dimensions of the OS - 12 "AYAKS", version 02